Factory Wholesale Fire Alarm Emergency Button/resettable Manual Call Point fire Alarm Push Button
Fire Alarm Manual Pull Station
The manual pull station provide a textured finger-hold area that includes Braille text. In addition to PUSH IN and PULL DOWN text, there are arrows indicating how to operate the station, provided for non-English-speaking people.
Pushing in and then pulling down on the handle activates the normally-open alarm switch. Once latched in the down position , the word" ACTIVATED" appears at the top in bright yellow, with a portion of the handle protruding at the bottom as a visible flag.
Resetting the station is simple: insert the key, twist one quarter-turn, then open the station's front cover, causing the spring-loaded operation handle to return to its original position. The alarm switch can then be reset to its normal(non-alarm) position manually(by hand) or by closing the station's front cover, which automatically resets the switch.
Loop design and wiring:
The fire alarm control panel Zone wire can be connected to terminal loop(+), loop(-) unpolarized wire.
If the manual call point is in the end of the zone wire, a 5.6K resistance should be connected to terminal loop(+),loop(-).
Note: All wiring must conform to applicable local codes, ordinances, and regulations.
Mounting indoor wall
Attach mounting base to wall at 1.5 meter's high
Connect field wiring to terminals
To attach product to mounting base
Secure product by tightening the one mounting screws in the front of the product housing.
1 x Fire alarm call point
2 x Keys
1 x English manual