90~270 VAC, 50 Hz, 2.0 amps.
Wire size: minimum 14 AWG (2.0 mm2) with 600-volt insulation.
Sealed lead-acid batteries only.
Maximum charging circuit: 27.6VDC 0.8 amp for normal flat charge.
Maximum battery charger capacity: 18AH battery.
NOTE: two 4AH batteries can be housed in the cabinet. Larger
batteries require a separate battery box.
Total 24 V system power: 3.0 amps.
Notification appliance (signal) power: 2.5 amps.
Maximum current per NAC: 1.25 amps (expandable to 2.5amps).
Maximum battery charging capability: 18 AH.
Resettable four-wire smoke detector power 500 mA.
Non-resettable power 500 mA.
NOTE: Total current for auxiliary power outputs and two NACs must not exceed 3.0 amps. .
Integral Form-C Alarm, Trouble and Supervisory relays, rated at: 2.0 amps 30 VDC (resistive), 2.0 amps 30VAC (resistive).
CABINET AND MOUNTING
CABINET PHYSICAL DIMENSIONS: 40.0 cm high x 35.0 cm wide x 11.5 cm deep.
CARTON PACKAGE DIMENSIONS: 48.0 cm high x 42.0 cm wide x 18.5 cm deep.
CABINET NET WEIGH: 6.0 Kg. (without batteries).
CABINET GROSS WEIGH: 6.6 Kg. (without batteries).
MOUNTING: The cabinet mounts using two key slots at the top of the back and two additional 6.5mm diameter holes at the bottom.