1. Company Information
Forging ahead through the course of trial and hardship, the adventurous CA Fire protection Co., LTD founded in 2012,situated in NANAN, Quanzhou city, Fujian Province China, the famous hometown of overseas Chinese in the southeast coastline, which is also a professional enterprise specializing in R&D, production, sales and service of fire fighting equipments. On the basis of creating values for clients with products and service, the company keeps in step with the development trend of advanced manufacturing and inspection technologies, makes continuously the technical innovation and seeks the technology leadership and provides clients with superior products and service.
The products involve more than 100 specs of pressure proportioning tank, Foam bladder tank, foam generator, portable foam fire extinguishing installation, foam gun, foam nozzle, foam fire hydrant, foam fire hydrant cabinet, wet alarm valve, deluge alarm valve, pre-action valve, water flow indicator, sprinkler nozzle, signal butterfly valve, signal gate vale, outdoor fire hydrant, Siamese connection, fire hydrant cabinet, lined fire hose ,hose reel, indoor fire hydrant, water-stream nozzle, fire coupling and so on. These products are inspected qualified by national inspection center and have obtained the type approval of fine fighting products by Ministry of Public Security and the CCC compulsory certification of fire fighting products. The products are widely applied and get great recognition and appraisal by the clients in national major projects, large public places and specialized markets.
Hanker for the remarkable quality, serve wholeheartedly for you!
Enterprise credit rating certificate
Work safety standardization certificate
4. Product Description
Wet alarm valve usually has the same water pressure at two sides of the disc (water goes through the water pressure balance hole in the guide pipe to maintain the water pressure balance between the both sides of the disc).Due to the weight of the disc and the disc before and different total pressures between two sides of the disc, the disc keeps closed (the total pressure above the disc is greater than the total pressure below the valve core).When fire burst, sprinkler starts spraying water. The water pressure on the alarm valve drops as the water pressure in front of the valve disc is larger than that behind the valve disc. Therefore, the valve disc opens to supply water to the riser and pipe network. At the same time, water enters the delay device, pressure switch, hydraulic alarm bell and other facilities along the annular groove of the alarm valve to send a fire signal and start the fire pump.
|Specifications||Wet Alarm Valve ZSFZ||Wet Alarm Valve (Groove type) ZSFZ100(G)/ZSFZ150(G)|
|Working Pressure|| 1.6Mpa|| 1.6Mpa|
|Seal Test|| 3.2Mpa|| 3.2Mpa|
|Stress Test|| 6.4Mpa|| 6.4Mpa|
|Frictional Resistance|| <0.02Mpa|| <0.02Mpa|
6. Contact Us
Loy Chou (Mrs.)